(7) Pull either or both tank valve control levers to the ON position.
An overheated pump creates a potential fire hazard and will
cause pump damage. Do not- allow pump to run longer than one
minute with nozzles closed. Do not run pump with tank valves
(8) Insert dispensing nozzle into tank being fueled and squeeze the nozzle lever.
(9) Move ON-OFF-Switch to ON position.
When tank is-full, release nozzle lever.
Move ON-OFF switch to OFF position and store cable on truck.
Remove dispensing nozzle from tank, disconnect nozzle ground clamp or plug and rewind hose onto
Dipole tank valve control levers to OFF position.
Lead safety equipment and disconnect static ground as per paragraph 2-3.