Hose Reels, Spring and
A spring loaded mechanism can cause injury if a released in
an uncontrolled manner. The rewind spring is under high
tension when the dispensing hose is extended. This may
cause reel to rapidly rotate in reverse.
Visual and operational inspection. Check operation of dispensing hose
reels. Extend hoses and inspect as per item 1. Check that ratchet wheel will
hold reel from rotating. Notify next higher level of maintenance if hose
reels need repair.
Check nozzles for proper operation and leakage. Check screen for foreign
matter. Repair or replace defective nozzles (para. 4-10).
Static Discharge Reel
A spring loaded mechanism can cause injury if released in an
uncontrolled manner. The rewind spring is under high
tension when the cable is extended. Always take care when
working with the mechanism.
Check for broken clamp, cable or cable coating. Replace defective reel
Refer to TM 10-4330-232-12&P for procedures.
Water Detector Kit
Check pump and components for proper operation, damage or leakage.
Refer to Table 4-2 to troubleshoot.
Low voltage can cause severe shock, burns or death.
Disconnect power cable from NATO slave receptacle before
replacing or repairing electrical components.
Check for damaged cables, loose connections, switch or connectors.
Check for damaged receptacles, housing, or cover gasket. Inspect relay
switch and connections inside the junction box for loose connections and
corrosion. Clean corroded connections, replace defective parts and
tighten loose connections. Refer to para. 4-12 for maintenance.