Table 2-1. Preventive Maintenance Checks and Services - Continued
ITEM TO BE INSPECTED
CENTRIFUGAL PUMP ASSEMBLY
When draining, do not smoke or use open flame in the
area. Always make metal-to metal contact between
the container and the fuel hose. This will prevent a
spark as fuel flows over metallic surfaces Failure to
observe this warning may result in death to person-
When pump is not in use, water should be drained.
Check that pipe cap (1) is securely installed.
Look through suction port and check for damage to suc-
tion check valve (2).
Visually check interior of suction port for foreign matter
that could enter into pump during operation.
Not Fully Mission
Drain plug is not prop-
erly installed. Notify
Suction check valve is
damaged. Notify Unit
Suction line is dogged
with foreign matter.
Notify Unit Mainte-