Alternate nozzle for dispensing unleaded fuel is listed in Appendix D, Additional
Authorized List, Sec. II, Item 2.
(f) Insert nozzles in vehicle or equipment fuel tanks carefully. Observe safe fueling rates stenciled near fuel
Be sure nozzle is operating correctly before starting electric motor.
(g) Open the tank dispensing valve and place motor start switch in the ON position (figure 2-1).
Continuous operation of the motor for more than 30 minutes will cause the
thermo protector to activate. The motor will then shut off until it is cool.
(h) Turn switch OFF when not dispensing fuel.
Opening tank dispensing valve on full tanks should prime the pump. If not,
manual priming can be done through the priming port (figures 1-4 and 1-5).
(i) The float ball inside the water sight gage window located on the filter/separator should not be above the
line mark on the window (figure 2-4).
(j) Check the window frequently for the location of the float ball and drain the filter/separator when the ball
reaches the line mark on the window.
Figure 2-4. Sight Gage.