a. Test for continuity.
Use multimeter to check both positive and negative sides of the connector. There should be a zero
resistance reading. If the reading is other than 0 ohms, replace defective parts. (See figure 4-20.)
Figure 4-20. Test for Continuity.
b. Connector Assembly Removal. (See figure 4-21.)
(1) Remove the cover from connector by removing screws.
(2) Remove the cables from connector by removing bolt and Iockwashers.
c. Connector Assembly Replacement. (See figure 4-21.)
(1) Attach cables to connector with Iockwashers and bolts.
(2) Attach cover to connector with screws.