TM 5-4320-275-13 & P
Table 4-1. Operational Checks - Continued
Check drive operation.
Operation should be smooth.
Replace noisy parts.
Check pump for leaks or rust.
Pump should be free of leaks and rust.
Replace defective parts.
Check pump output.
Pump should deliver approximately 100 gpm (38400 phr).
Section IV. PREVENTIVE MAINTENANCE CHECKS AND SERVICES
4-7. PREVENTIVE MAINTENANCE CHECKS AND SERVICES
Table 4-2 lists the preventive maintenance checks and services which shall
at specified intervals
organizational maintenance personnel. It includes and expands upon the preventive maintenance services performed by
operator/crew maintenance and includes additional services which are allocated to organizational maintenance.
Item numbers in the following table shall be used as source of item numbers for the TM
Number Column on DA Form 2404, Equipment Inspection and Maintenance Worksheet, in
recording results of PMCS.