Inspect nozzle body (5) and spout (1) for damage. Check free operation of lever (20).
Inspect coupling half (6) for any damage. Check the gasket (7) and replace if damaged.
Check grounding wires (12 and 14) for breaks, fraying and broken or missing covering. Make sure clip
(13) jaws close firmly and inspect plug (11) and nut (10) for any damage. If clip (13) or wire (12) are defective,
replace complete static discharger (8).
Do not shorten grounding wire to less than 18 inches between
contact and clip.
If grounding wire (14) is broken or frayed at the contact (9) it may be repaired. Hold nut (19) and
unscrew contact (9). Pull nut from wire (14) and cut off the frayed portion of the wire. Trim plastic cover from
the end of wire and slide nut (19) over the end of wire (14), allowing approximately 1/4 inch of wire to extend
through nut. Use a punch, or similar toot, to spread the end of wire (14) slightly, then screw contact (9) onto nut
If nut (10) was removed, use the same procedure as above to install it on wire (12).
Compressed air used for cleaning can create airborne particles
that may enter the eyes. Pressure will not exceed 30 psig. Eye
Use low pressure compressed air to dry strainer element (4) and remove any trapped particles.
Replace the strainer element if there is damage to the screen.
Replace any other parts that are damaged. Use a new O-ring packing (2) and gasket (3) at assembly.
Silicone compound, MIL-S-8660, is toxic to skin, eyes and
respiratory tract. Skin and eye protection required. Avoid
repeated or prolonged contact. Good general ventilation is
Apply silicone compound to O-ring packing (2) and install it on strainer element (4).
Install strainer element (4) and gasket (3) on spout (1) and screw spout into nozzle body (5), hand
Screw plug (11) onto nut (10) and install the static discharger (8) by screwing contact (9) into nozzle
Connect chain (15) and spring (16) to e-hooks (17) and squeeze the e-hook closed. Connect the s-
hooks to the body (5) and cap (18) and squeeze closed. Install the cap (18) on spout (1).
Apply sealing compound to threads of coupling half (6) and screw coupling half into body (5). Install