Dry cleaning solvent, P-D-680, used to clean parts is potentially
dangerous to personnel and property. Avoid repeated and
prolonged skin contact. Do not use near open flame or
excessive heat. Flash point of solvent is 100 degrees F-138
degrees F (38 degrees C-59 degrees C).
Clean all metal parts with dry cleaning solvent and dry thorough 9.
Inspect parts for damage and replace parts as required.
Inspect fuel passage for obstructions.
Install tray (15) on sensor (16) and install flat washers (14) and screws (13).
Assemble deflector shield (11) to sensor (16) and position on bracket (12) with mounting holes alined.
Install lockwashers (10) and capscrews (9)
Connect hose (8) with clamp (7).
While holding jet level sensor (6) in manhole
(1), note the tube (4) marked inlet! then attach inlet tube
to jet level sensor inlet. Attach remaining tube (4).
Position jet level sensor (6) within tank and
secure with capscrews (2) and lockwashers (3).
Close and latch manhole (1).