Table 2-1. Preventive Maintenance Checks and Services - Continued
ITEM TO BE INSPECTED
CENTRIFUGAL PUMP ASSEMBLY
When draining, do not smoke or use open flame in
the area. Always make metal-to-metal contact be-
tween the container and the fuel hose. This will pre-
vent a spark as fuel flows over metallic surfaces.
Failure to observe this warning may result in death
When pump is not in use, water/fuel should be
Inspect for dogged or damaged spark arrestor.
Check that pipe cap (1) is securely installed.
Look through suction port and check for damage to suc-
tion check valve (2).
Visually check interior of suction port for foreign mater
that could enter into pump during operation.
Not Fully Mission
Drain plug is not prop-
erly installed. Notify
Suction check valve is
damaged. Notify Unit
Suction line is dogged
with foreign matter.
Notify Unit Mainte-